CAREL Remote Terminal-MCH2 Carel MCH200TP00 chiller and AHU controller in bd. The carel provided is Chiller, Air Handeling Unit-AHU, HVAC & Compressor and Colling system device is worldwide.
Maximum voltage threshold for Triac F04:
In the event of fan speed control, the optional phase cutting cards (MCHRTF*) are required, fitted
with a triac. Which is CAREL Remote Terminal-MCH2 Carel MCH200TP00 chiller and AHU
F04 = Represents the maximum threshold for the triac
Temperature/pressure set point is minimum speed in cooling, F05: This represents the temperature or pressure below which the fans remain ON at minimum speed.
Temperature/pressure differential for maximum speed in cooling F06:
At this represents the temperature or pressure differential in reference to F05 above which the fans are
started at maximum speed; in the case of ON/OFF control, this represents the differential.
Temperature/pressure differential for fans Off in cooling F07:
This represents the temperature or pressure differential in reference to F05 below which the fans
are stopped. The fans are started 1 °C “lower” when using NTC temperature probes, or 0. 5 bars if using